WAZIPOINT Engineering Science & Technology: Underground Power Cable Bonding Methods

## Monday, October 31, 2022

### Underground Power Cable Bonding Methods

 Cross bonding for high voltage underground cable sheath earthing

Widely used bonding system for High Voltage or Extra High Voltage power cables are as follows:
1. Both End Bonding Systems
2. Single Point Bonding System
3. Cross Bonding System
4. Both End Bonding systems

The simplest arrangement to eliminate sheath induced voltage is Both End Bonding system. It is very easy and simple to ground both end of cable sheath. Minimum materials are required which lead to economical.

But circulating current flows through cable sheath and heat produces which increase loss and reduce cable life. Circulating current is proportional to the length of the cable and the magnitude of the load current. This system normally applies to short cable section of tens of meters long.

### Single point bonded system

A simple system is single point bonding which arrangement does not allow any path to flow circulating currents or external fault currents. In this system the sheaths of cables are grounded at one end and other end are open or connected with SVL and grounded through earth continuity cable, consequently induced voltage is present at open end.

The magnitude of sheath induced voltage depends on the length of the cable, longer the cable length higher the induced voltage. Using of this bonding system is limited only for short distance of cable length to keep induced sheath voltage within a safe limit. Generally suitable for less than 500 m cable length.

### Advantages of Single Point Bonding:

No circulating current.
No heating in the cable screen.
Economical
Induced voltage at the un–earthed end
SVL required if induced sheath voltage during fault is extreme.

### Cross Bonding system

This arrangement is such that the circuit provides electrically continuous sheath runs from earthed termination to earthed termination. Voltage will be induced between screen and earth, but sectionalized cross bonding system will reduce the sheath circulating currents.

Screen separation and additional link boxes are require for this system, arrangement carries 3 minor sections in each major section. When number of minor sections is not exactly divisible by 3, then system may consist of mixture of single point bonding with cross bonding. This system is technically complicated and more expensive, but for long route length cross bonding system is suitable because of following advantages-

-Earth continuity conductor no need.

-Virtually zero circulating current in the screen.

-Standing induced voltage in the sheath is controlled.

-Technically superior than other methods.

-Suitable for long route length.

1. I am working on the British Essay Writers In UK to the UK students in the reasonable prices.

2. With this configuration, the circuit offers electrically continuous sheath runs from one earthed termination to the next. Although sectionalized cross bonding may lessen the sheath circulating currents, voltage will be induced between the screen and the earth.

3. This blog is really amazing specially if you are studying mechanical engineering. My friend also studies Mechanical but he hires expert and say him to take my online class and then guide briefly.

4. Essay writing service from experts. Hire experienced writers and get higher grades on the essay. 24/7 available. Visit the site.

5. Yes! You can. We guarantee an overall score of 90% or your money back. Our expert tutors will help you succeed on your take my teas exam for me.

6. I can't express how much I appreciate this article and the Petit Fernand Discount Codes you've provided. You're a true hero for helping us all save money and get the best deals!

WAZIPOINT:
Thank you very much to visit and valuable comments on this blog post. Keep in touch for next and new article. Share your friends and well-wisher, share your idea to worldwide.